RO Pre & Post Treatment
Where RO membranes are used it is advised to prefilter the feed water to remove particulate matter that could foul the membrane. RO membranes are constructed as a spiral wrap and so there is no easy method to remove particulates that may have entered the RO filter. Prefilters will reduce the particulate load entering the RO filter so that the RO membrane can perform at its optimum output.
If thin film composite (TFM or TFC) RO membranes are used, carbon prefiltration should be used to remove chlorine from the incoming water since chlorine attacks the TFM membrane material. However, if cellulose triacetate (CTA) RO membranes are used, carbon prefilters are not required since these are not at risk from chlorine.
Ion exchange products can enhance pre-treatment to the RO membranes. One of Graver’s Ecodex powdered ion exchange resin products can be applied to RO prefilters to remove objectionable ionic and some organic species to help limit RO membrane fouling. Ecosorb products are also useful for reduction of organics.
While RO membranes can remove some heavy metal contaminants such as arsenic V, they are ineffective at removing arsenic III. Graver Metsorb HMRG is a highly specialized adsorbant material that effectively removes arsenic III, as well as arsenic V, lead and other heavy metals. Placed downstream of the RO membrane, Metsorb HMRG adsorbent can achieve the water purity required for your end use.
Graver Product Selection
|MBF™ or STC™
||Melt blown depth filters for Pre RO filtration to prevent membrane fouling. 5 micron is most typically used.
||Carbtec extruded carbon block filters effectively remove chlorine to protect TFC type RO membranes.
||Apply Ecodex to the top of sand filters as a precoated layer up to several inches in depth to remove ionic contaminants and some organics
||Apply in the same manner as Ecodex to enhance organic removal. Ecodex and Ecosorb may be used together.
||Highly specialized adsorbent material removes heavy metals, lead and arsenic III and arsenic V from water. Use downstream of the RO membrane.